Rainwater harvesting/Surface water/Protected side intake
A protected side intake provides a stable place in the bank of a river or lake, from where water can flow into a channel or enter the suction pipe of a pump. It is built to withstand damage by floods and to minimize problems caused by sediment. Side intakes are sturdy structures, usually made of reinforced concrete, and may have valves or sluices to flush any sediment that might settle. Often, a protected side intake is combined with a weir in the river to keep the water at the required level, a sand trap to let the sand settle, and a spillway to release excess water. The river water may enter the side intake through a screen, and a spillway overflow may be provided. Sometimes, protected side intakes are combined with a dam and a flushing sluice, which allows the upstream part of the river to be flushed.
- The main purpose of an intake is to ensure a constant water supply that can be adjusted to suit local conditions.
- Avoid large rivers with a fluctuating water level. Be very careful to make sure the intake is not set above the minimum water level of the river.
Resilience to changes in the environment
Drought effects on cement
Effects of drought: When water levels are low, problems can occur if the concrete was badly made, which also leads to cracked linings (e.g. in tanks, dams, waterways, wells, and other structures).
Underlying causes of effects: Less water used for curing; Impure water used for mixing.
To increase resiliency of WASH system: Ensure adequate mixing, ratios, purity of ingredients; Minimize water content in mixture; Ensure adequate curing.
More information on managing drought: Resilient WASH systems in drought-prone areas.
Construction, operations and maintenance
— Operation of a protected side-intake system is usually carried out by a caretaker;
— a valve or a sluice may have to be adjusted daily, the inlet to the channel or pump checked for obstructing debris, and any damage repaired;
— preventive maintenance, including painting the screens and other metal parts, such as sluices or valves;
— the intake canal and silt trap may have to be de-silted, debris cleaned from the screens regularly, and damaged screens should be welded;
— during the rainy season, the inlet may need checking and cleaning more frequently;
— any erosion of the river bank or bed must be repaired immediately with boulders, rocks, sandbags, etc.;
— cracks in the concrete structure should be repaired every year;
— annual cleaning and major repairs (these may require the assistance of the water users);
— after flooding, cleaning may be necessary.
— clogging by silt or debris;
— the side-intake system may be undermined by river currents;
— the river or lake water may be polluted.
- Surface water intake and small dams. Chapter 11. Revised by Nhamo Masanganise.
- Brikke, François, and Bredero, Maarten. Linking technology choice with operation and maintenance in the context of community water supply and sanitation: A reference document for planners and project staff or (alternative link). World Health Organization and IRC Water and Sanitation Centre. Geneva, Switzerland 2003.
- CARE Nederland, Desk Study: Resilient WASH systems in drought-prone areas. October 2010.
- Original Akvopedia.org article: Protected side intake